We are happy to inform our colleagues about the next Ekoton’s successful installation in Chile.
In 2017 the dissolved air flotation complex for local wastewater treatment of a fish processing plant in Los Lagos region had been installed by our partner Aguas Sipra S.A., including such equipment as:
- Fine drum screen RMB TP 6/6,
- DAF unit FT-25,
- Tubular flocculator,
- Saturation system for white water preparing,
- Pumps for the complex,
- Automation system for the complex, including control system with sensors.
The Ekoton DAF complex has a customized design for the particular application. The object’s features required high amounts of dissolved air to be fed into wastewater to tackle high loads of contaminants. The complex’s capacity is 18 m3/h.
The efficiency of the complex is as follows:
Los Lagos, Chilie Project Data
|Parameters||Input concentration, [mg/L]||Efficiency, [%]||Output concentration, [mg/L]|
|Total suspended solids (TSS)||6,541||95||327|
|Biochemical Oxygen Demand (BOD5)||10,696||40||6,418|
|Nitrogen, Total Kjeldahi (NTK)||726||20||581|
|Oil and Grace (O&G)||975||90||98|
|Dissolved solids (DS)||81||60||32|
As a result the customer got a specially designed wastewater treatment system which is fully solves its effluent requirements. In this project Ekoton confirms the advantages of it’s developed DAF technology as well as the appropriateness of approach to use just the highest quality components available. The equipment operates steadily well, which is really important for such a distant projects.
More information about project in REVISTA INDUAMBIENTE Ed. N°148 / Sep-Oct 2017, p.42-43