SIZE OF WWTP 10 000 m3/day (2 641 000 GPD)
END USER Water and wastewater utility provider, OAO Vodokanal
CUSTOMER OOO SibKapStroy
START OF OPERATION August, 2017
In Gorno-Altaysk WWTP, instead of mechanical sludge dewatering, sludge was dewatered in outdated sludge drying beds. Malodor from sludge drying beds disturbed residents from nearby leaving area, therefore regional authorities made a decision to fund the construction of a new sludge dewatering facility.
Based on national requirements, 3 units (2 duty and 1 stand-by) of MDQ-352 C were installed.
|Type of sludge||Mixture of primary sludge and|
waste activated sludge
|Unit Sludge Supply||3-3.5 m3/h (13-15 GPM)|
150-160 kg DS/h (330-350 lb DS/h)
|Feed Sludge DS Concentration||4-6 %|
|Cake DS Concentration||23-27 %|
|Opetarion time||10 h/d|
|Average Polymer Dose||3.5-4.5 g/kg DS (7-9 lb/ton DS)|
|Unit Daily Power Consumption||18 kW*h|