SIZE OF WWTP 6000 m3/day (1 585 000 GPD)
END USER Poultry slaughterhouse, PrAT Myronivska Poultry Farm
CUSTOMER PAT Myronivsky Hliboproduct
START OF OPERATION December, 2015
Increased capacity of a slaughterhouse resulted in an increased amount of sewage sludge. An existing dehydrator was not able to handle this increase alone, therefore a call for bids was issued.
EKOTON submitted a lowest priced bid for a modern complex sludge dewatering solution with a state-of-the-art automation system based on PLC and HMI and won the bidding. One unit of MDQ-353 C was installed in parallel with an existing dehydrator from other manufacturer. Having similar nominal capacity, our MDQ achieves higher cake DS content compared to an existing dehydrator.
|Type of sludge||DAF sludge|
|Unit Sludge Supply||6-7.5 m3/h (26-33 GPM)|
700-750 kg DS/h (1540-1650 lb DS/h)
|Feed Sludge DS Concentration||8-12 %|
|Cake DS Concentration||33-40 %|
|Operation Time||14-18 h/day|
|Average Polymer Dose||2.2 g/kg DS (4.4 lb/ton DS)|
|Unit Daily Power Consumption||35-45 kW*h|