Mechanical dewatering equipment
The thickener is intended for mechanical dewatering of wastewater, as well as water conditioning and purification of sludge and industrial slimes. The thickeners can also be used in a first stage dewatering role, together with filter presses for filter press productivity improvement with initial sludge. The thickeners are intended for use in wastewater sludge with a pH of 6.0 - 9.0.
The thickener is manufactured from stainless steel AISI 304.
The thickener features a strained, endless sieve belt with an installed ripper system on it. The flushing unit, sludge feeder and distributor and the filter cake removal device are provided with the filter press.
In the “Comby” version, the thickener is installed onto the frame of the filter press: thickened sludge removal is carried out onto the filter press belt for further dewatering.
The thickener operates in continuous mode.
The sludge / flocculent mixture is fed to the moving top sieve belt and distributed all over its operating length. In the movement, the sludge layer is constantly mixed by the ripper system for water outflow improvement. The water drains via gravity feed. The dewatered filter cake is then removed from the belt by polymeric scrapers into the receiving bin. The thickener is flushed by water under pressure in the flushing zone after the filter cake removal.
After dewatering in the thickener, the sludge moisture can be reduced from 98-99% to 90-96% - i.e. decrease of sludge volume of 3-10 times occurs.
The filter presses are provided with drives, belt position-, speed- and tension control system sensors and an air pressure loss protection system. It allows complete automation of the dewatering units on the basis of filter presses to implement.
All electric sensors and drives have a high level of protection against moisture and ambient air corrosive action.
An indication system of normal operation and emergency situations is provided.It is possible to transfer equipment status data to a higher level automated process control system depending on the client’s requirements.
|Capacity by dry matter, up to more [kg/h]||600...1100|
|Capacity by initial sludge, up to more [m3/h]||30...50|
|Belt width, [mm]||1200...2000|
|Belt velocity, [m/min]||2...10|
|Drive power, [kW]||1,1|